Waste heat Recovery
Utilisation of industrial waste heat
The utilisation of waste energy in industrial enterprises has enormous potential in terms of energy efficiency, the exploitation of which delivers both positive ecological and economic benefits.
- Heat recovery / displacement
- Using waste heat in electricity production
- Waste heat utilisation using a steam turbine
- ORC - Organic Rankine Cycle
- Waste heat utilisation for cooling and air conditioning
- Waste heat utilisation using heat pumps
- Specialist technologies
- Temperature level
- Waste heat thermal output
- Simultaneity of potential and demand
- Utilisation period
- Other factors relevant to the exploitation of waste heat
In these days of mounting environmental awareness and more intensive discussions on the subject of sustainability and the concomitant conservation of fossil fuels, the energy industry is focusing increasingly on the topic of energy efficiency. Both of these topics are intimately entwined. There are two options for increasing the energy efficiency of power production facilities. In addition to renovation or modernisation of the plant and depending upon the specific circumstances, the utilisation of hitherto neglected energy potentials, such as waste heat, can contribute to a net increase in the energy yield from the primary energy carriers and therefore to increased energy efficiency.
The term 'waste heat' refers to any heat generated by a living organism, technical plant or process, which is dissipated into the surrounding environment without being used. It is created through inefficient facilities or process management as well as through thermodynamic constraints.
It is classified with reference to the prevailing temperature level in accordance with the following scheme:
- Low temperature waste heat: < 150 °C
- Medium temperature waste heat: 150 °C-500 °C
- High temperature waste heat: > 500 °C
The greatest untapped waste heat potential is to be found in the industrial sector. Extremely energy-intensive production processes are especially prone to the creation of heat loss sources, in which useful energy generated from primary energy carriers is dissipated into the surrounding environment as industrial thermal waste.
The following example shows the waste heat temperature levels for certain industrial sectors.
|Temperature level||Industrial sector|
|High temperature||Pig iron industry|
|Medium temperature||Printing and publishing industry|
|Low temperature||In practically every industrial sector|
In the majority of cases it only makes economic sense to exploit waste heat potentials in the medium to high-temperature range.
Technologies for the exploitation of industrial waste heat
There are many technologies available for converting hitherto unused energy into usable energy. The following is an overview of the most important technologies and approaches.
Heat recovery / displacement
This is the most efficient and, at the same time, simplest technological approach to waste heat recovery. The waste heat, for example from an exhaust flow, is extracted via a heat exchanger and transferred to a different medium, whereby the heat transfer medium may be hot water, thermal oil, steam or a gaseous fluid. The transferred heat is transported via the heat transfer medium to existing heat sinks for further utilisation.
Which heat transfer medium is most appropriate in any given case and which parameters (pressure, temperature etc.) are required, will depend upon the available heat sinks. In this way the waste heat can be used as a substitute for primary energy carriers to generate process heating in the form of steam or thermal oil. Another area of application is the provision of heating energy. The supply of recovered waste heat into an existing district heating grid is promoted in the context of the national KfW (Credit Bank for Reconstruction)-sponsored energy efficiency program “Waste heat”. For example, in production processes involving firings and the use of furnaces, this extracted waste heat can be used to preheat the combustion air, which itself reduces the level of primary energy carrier consumption. Waste heat utilisation through direct heat recovery and heat displacement is characterised by a high level of efficiency. The associated losses are restricted to those that occur during the thermal transfer process. From an economic perspective the financial expenditure is relatively low compared to the energy gains.
Converting waste heat into electricity
Converting waste heat into electricity follows the same basic principles as the previously noted energy recovery concept. In the absence of heat sinks capable of being serviced by the energy generated from waste heat, the heat transfer medium can be used for conversion to electrical energy. Two main technologies are used to convert waste heat into electricity. Either the conversion is achieved via a closed water/steam circuit using a steam turbine or else a thermal oil or hot water circuit feeds into an Organic Rankine Cycle (ORC) in order to generate electricity.
Waste heat utilisation using a steam turbine
Using a steam turbine to convert waste heat into electricity involves the generation of steam, which is released via a steam turbine. This in turn generates electricity, which can, for example, be fed into a site grid in partial fulfilment of the overall power demand. This reduces the amount of electricity drawn from the national grid and lowers the associated costs accordingly. Because steam power production is relatively material intensive due to the low exergy and the efficiency factor of the steam turbines is strongly dependent on the steam parameters such as temperature and pressure, steam turbines are usually only used to convert waste heat to electricity when the waste heat temperature exceeds 300 °C. The efficiency factor of the steam turbines is between 20 and 30%.
ORC - Organic Rankine Cycle
In essence, the generation of electrical power from waste heat using ORC largely functions in the same way as a steam turbine. It only differs from the steam turbine in terms of the working fluid, which, in the case of ORC, consists of an organic medium instead of the water used by the steam turbine. The thermodynamic characteristics of this organic medium differ from those of water as a result of which it can be vaporised at lower temperatures and at lower pressures. This is why ORC can be used for electrical energy generation in conjunction with waste heat temperatures of 90 °C and above. Depending upon the temperature level, an ORC can be used to achieve an efficiency factor of 24%.
Waste heat utilisation for cooling and air conditioning
It is also possible to use waste heat for cooling and air conditioning purposes either at the building level or for individual process steps. To this end the waste heat is extracted in order to transfer low temperature heat to a heat transfer medium. The low temperature heat this makes available can then be used within a sorption chiller to produce cold water.
Within the sorption chillers, cold water is produced via absorption or adsorption processes, which is then available to be used as required. In this way it is possible to substitute cooling from traditional compression refrigeration units and to save the corresponding power consumption.
Waste heat utilisation using heat pumps
This method involves increasing the temperature level of the useful heat generated by augmenting it with higher-value energy in order to make it usable. This higher-value energy could be either electrical power or heat from a high-temperature source which is potentiated using compression or sorption heat pumps in order, for example, to cover the heating requirements of a given property or of a production process.
In addition to the above mentioned technologies for industrial heat recovery, there are a range of other technologies that are used less frequently due to certain special parameters.
These include, for example:
- The conversion of waste heat to electricity using the Stirling engine
- The conversion of waste heat to electricity using thermoelectric elements (Seebeck Effect)
- Heat transformation
In terms of deciding which specific technology can be used for heat recovery purposes, there are a number of criteria that can be applied to restrict the range of potential technologies.
The temperature level of the available waste heat source is one of the most important factors when choosing the most appropriate technology for industrial waste heat recovery.
In general, it is true to say that it only makes economic sense to consider the generation of electrical power from waste heat in the medium to high temperature range. Low temperature waste heat can also be used for heat pumps, chiller units and heat transformation processes. Heat recovery/displacement is possible at all temperature levels.
The following graphic shows the various technologies arranged by temperature level as well as by plant power output (in terms of the usable energy yield).
Waste heat thermal output
The waste heat thermal output is a crucial factor in terms of plant dimensions and the economic case for a waste heat energy plant. The higher the available waste heat thermal output, the higher the energy yield will also be.
The waste heat thermal output is primarily dependent upon the following factors:
- Volume flow (exhaust gas, fluid)
- Pre heat transfer medium temperature
- Potential post heat transfer medium temperature
- Composition of the exhaust gas/fluid
The waste heat thermal output can be calculated from the pre and post thermal transfer medium temperature difference together with the volume flow. The composition of the exhaust gas/fluid has a decisive influence on its energy content and therefore also on the extractable thermal yield. In addition, the mixture could contain corrosive substances, which need to be taken into consideration when selecting the material for the heat transfer medium and may have an impact on the investment costs.
Simultaneity of potential and demand
For an optimum and simple industrial waste heat utilisation it is advantageous if the heat supply from waste heat recovery exactly matches the energy requirements. If not, then storage media need to be employed as buffers. At this point in time, the use of storage with waste heat to electricity conversion technologies is not economically viable. For this reason, any excess energy not consumed must be fed into the national grid. In principle, it is also possible to operate the heat recovery plant under partial loading conditions.
The utilisation period of a given waste heat recovery plant depends directly upon the availability of the waste heat source. To operate a waste heat recovery plant on an economically sound basis, it is crucial to ensure as continuous and lengthy a utilisation period as possible. The financial outlay for the waste heat recovery plant will be recouped through the usable energy volume yield. This means that, the longer the utilisation period, the shorter will be the amortisation period.
Non-continuous availability of the waste heat source results in more power-up and power-down processes within the waste heat recovery plant. This subjects the material to increased thermal stresses, which can, in turn, result in higher maintenance and repair costs at the waste heat conversion plant.
Beyond the above mentioned criteria there are a number of additional factors which have a bearing on the choice of technology both from an energetic and an economic standpoint. Among these are the local spatial conditions. To minimise the investment costs, the source of the waste heat should ideally be close to the heat sink.
A further consideration is concentration. It is significantly easier and more cost effective to exploit a single concentrated waste heat source than several distributed sources.
Ecological and economic benefits of waste heat utilisation
From an ecological perspective, the generation of useful energy from waste heat is carbon neutral. No additional primary energy carriers are introduced for the conversion of waste heat into usable energy. Another ecological consideration is the fact that the useful energy gained through this technology substitutes that which would have been consumed from other energy sources that do consume primary energy carriers during the conversion process. This substitution reduces the utilisation of primary energy sources, for example, in the production of process heating, electricity or heating.
In addition, this energy substitution has economic effects. By saving the thermal or electrical energy that would have to have been supplied through alternative energy production processes, the cost of fuel or electrical power can also be saved. Energy expenditure is often a significant cost factor, which directly influences the ability of production firms to compete in the market. By contrast with the consumption of energy from public sources, the costs associated with the conversion of waste heat to usable energy can be calculated over the long term. This reduced the dependency on the energy markets and the concomitant risk of unpredictable price increases. Over and above this, the provision of process heating through waste heat exploitation can result in a lower CO2 certificate quantity requirement, which, in turn, results in cost savings.
GETEC heat & power GmbH – Your partner for industrial waste heat recovery
The heat recovery industry has an enormous potential to significantly increase the energy efficiency of production processes and to reduce the use of fossil fuels. The technologies used by GETEC heat & power for the utilisation of waste heat are all proven and robust applications, comprising state-of-the-art technology capable of sustaining lengthy utilisation periods. Waste heat recovery is a sustainable, environmentally-friendly way to conserve resources whilst increasing energy efficiency.
The cost of fossil fuels will increase over the long term. This trend can be countered by the use of a waste heat recovery plant, which lowers fuel costs and reduces dependency on public supply markets by the in-house production of usable energy. Why not reap the benefits of GETEC heat & power's long-term know-how?
Curious about waste heat recovery for industrial enterprises using technologies from GETEC heat & power GmbH? Contact us by e-mail on firstname.lastname@example.org or give us a call!
Would you like to learn more about the ORC process and its application? Learn more